By Linda Cerise. Electrical Wiring. Publised at Saturday, January 27th 2018, 05:30:58 AM. Every type of machine has unique requirements when it comes to operator safety. From an electrical standpoint, industrial machine equipment and tools - from drill presses to multi-motored automatic machines.
By Augustine Yvonne. Electrical Wiring. Publised at Wednesday, January 24th 2018, 11:53:01 AM. You must totally enclose conductors and their connection external to the control panel enclosure in suitable raceways or enclosures. Unless used for flexible connections involving small or infrequent movements, or connections to normally stationary motors, limit switches and other externally mounted devices, fittings used with raceways or multiconductor cables must be liquidtight.
By Linda Cerise. Engine Wiring. Published at Sunday, February 11th 2018, 13:58:59 PM. When your engine is operating, your stator produces an alternating current by means of electromagnetic induction. This alternating current is fed to your rectifier/regulator by two wires. These two stator wires connect to the AC – and AC + terminals on the rectifier/regulator. The rectifier/regulator converts the alternating current into a direct current and is fed out of it through the terminal marked B+. This wire leads to the “rectifier or R” terminal on your ignition switch. This direct current charges your battery.
By Linda Cerise. Electrical Wiring. Published at Sunday, February 11th 2018, 13:20:01 PM. Conductors and cables should run from terminal to terminal without any intervening joins. This refers to making a joint in the middle of a wire or cable. If it is necessary for any reason then use a suitable connector or terminal block. Don’t use a twisted and soldered joint.
By Babette Benjamine. Electrical Wiring. Published at Sunday, February 11th 2018, 10:57:22 AM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Babette Benjamine. Electrical Wiring. Published at Sunday, February 11th 2018, 10:19:33 AM. The combined cross-sectional area of all conductors and cables is not permitted to exceed 50% of the interior cross-sectional area of the raceway. The fill provisions are based on the actual dimensions of the conductors or cables used.
By Sylviane Marcelline. Electrical Wiring. Published at Sunday, February 11th 2018, 09:43:11 AM. Modern electrical machine tool equipment may vary from that of a single-motor machine (such as a drill press that performs simple, repetitive operations) to very large, multimotored automatic machines, which contain highly complex electrical control systems. Typically, these machines are especially designed, factory-wired, tested by the builder and then erected in the plant.
By Linda Cerise. Electrical Wiring. Published at Sunday, February 11th 2018, 08:29:36 AM. This section requires you to support conductors in panels to keep them in place. You're permitted to use wiring channels if they're made of a flame-retardant insulating material. If you're working with back-connected control panels, you must provide access doors or swing out panels that swing about a vertical axis. Multiple-device control panels must have terminal blocks or attachment plugs and receptacles to terminate and connect all outgoing control conductors.
By Annette Noele. Electrical Wiring. Published at Sunday, February 11th 2018, 07:33:20 AM. When the current is switched on or off, the electro-magnetic field increases and decreases, rapidly causing, in effect, a radio signal. The effect is similar to the crackle that can sometimes be heard on the radio or television when something like a fridge switches on and off. This radiated signal can be picked up by the other wires in the system and cause interference to the normal working voltages in the system
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.