By Augustine Yvonne. Electrical Wiring. Publised at Wednesday, October 18th 2017, 14:48:20 PM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Blandine Honorine. Electrical Wiring. Published at Monday, January 29th 2018, 04:31:51 AM. Connections should be secured against accidental loosening. Correctly tighten terminal screws and where a connecting plug is fitted, use the clamps or screws provided to secure it to its mating socket.
By Severin Theodore. Electrical Wiring. Published at Monday, January 29th 2018, 03:26:36 AM. A lamp inside an enclosure provided for use during maintenance is an example of such a circuit. The control panel may be isolated but the lamp will require power so that the engineer can see while working on it.
By Blandine Honorine. Electrical Wiring. Published at Sunday, January 28th 2018, 23:39:19 PM. Where the circuits work at different voltages, the conductors must be separated by suitable barriers or all the wires insulated for the highest voltage to which any conductor may be subjected.
By Severin Theodore. Electrical Wiring. Published at Sunday, January 28th 2018, 21:58:26 PM. Conductors and cables should run from terminal to terminal without any intervening joins. This refers to making a joint in the middle of a wire or cable. If it is necessary for any reason then use a suitable connector or terminal block. Don’t use a twisted and soldered joint.
By Annette Noele. Electrical Wiring. Published at Sunday, January 28th 2018, 19:28:59 PM. You are required to use pressure connectors to connect conductors to devices with lug-type terminals that are not equipped with saddle straps or equivalent means of retaining conductor strands.
By Augustine Yvonne. Electrical Wiring. Published at Sunday, January 28th 2018, 19:18:48 PM. When the current is switched on or off, the electro-magnetic field increases and decreases, rapidly causing, in effect, a radio signal. The effect is similar to the crackle that can sometimes be heard on the radio or television when something like a fridge switches on and off. This radiated signal can be picked up by the other wires in the system and cause interference to the normal working voltages in the system
By Annette Noele. Electrical Wiring. Published at Sunday, January 28th 2018, 18:50:48 PM. Modern electrical machine tool equipment may vary from that of a single-motor machine (such as a drill press that performs simple, repetitive operations) to very large, multimotored automatic machines, which contain highly complex electrical control systems. Typically, these machines are especially designed, factory-wired, tested by the builder and then erected in the plant.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.