By Annette Noele. Electrical Wiring. Publised at Thursday, February 01st 2018, 07:32:39 AM. You are required to run conductors and cables from terminal to terminal without splices. However, an exception allows you to install a splice in leads attached to electrical equipment, such as motors and solenoids.
By Claudie Ulysse. Electrical Wiring. Publised at Tuesday, February 06th 2018, 22:03:03 PM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Augustine Yvonne. Electrical Wiring. Publised at Tuesday, January 30th 2018, 16:32:34 PM. You are required to run conductors and cables from terminal to terminal without splices. However, an exception allows you to install a splice in leads attached to electrical equipment, such as motors and solenoids.
By Sylviane Marcelline. Electrical Wiring. Published at Monday, January 15th 2018, 17:39:06 PM. It is uncommon for engineers to build their own PLC panel designs (but not impossible of course). For example, once the electrical designs are complete, they must be built by an electrician. Therefore, it is your responsibility to effectively communicate your design intentions to the electricians through drawings.
By Charline Rodrigue. Electrical Wiring. Published at Monday, January 15th 2018, 16:20:30 PM. The terminations of shielded or screened conductors should be terminated so that the screen cannot fray. If the screen is to be connected then make it off in the same way as for coaxial cable with a soldered pigtail and a sleeve.
By Babette Benjamine. Engine Wiring. Published at Tuesday, January 09th 2018, 20:54:52 PM. Your ignition switch is a rotary switch that when turned to one of its 3 positions connects and disconnects certain contact terminals located on its backside. In the “start” position, it connects the Battery, Ignition, Rectifier, Accessory, and Start Terminals.
By Severin Theodore. Engine Wiring. Published at Sunday, January 07th 2018, 18:37:08 PM. The valve face is the area on the valve that makes contact with the valve seat. It can become worn, warped and pitted over time. In order to correct this you will need a valve face grinder. These are expensive tools, so I recommend replacing the valves with new ones when you can. The rest of this article will assume you are using brand new valves.
By Blandine Honorine. Engine Wiring. Published at Friday, January 05th 2018, 10:47:51 AM. So your tractor lost spark. You purchased a new ignition coil. After you installed it you still don’t have spark. What happened? We will go into this common problem later in the article, but for now remember never make assumptions. Always look for evidence that suggests a cause. Evidence comes in many forms such as smoke coming from your engine, metal particles in your oil, and oil leaks from your transmission.
By Annette Noele. Electrical Wiring. Published at Thursday, January 04th 2018, 08:16:01 AM. You are required to use pressure connectors to connect conductors to devices with lug-type terminals that are not equipped with saddle straps or equivalent means of retaining conductor strands.
By Augustine Yvonne. Electrical Wiring. Published at Tuesday, January 02nd 2018, 07:47:42 AM. The combined cross-sectional area of all conductors and cables is not permitted to exceed 50% of the interior cross-sectional area of the raceway. The fill provisions are based on the actual dimensions of the conductors or cables used.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.