By Charline Rodrigue. Electrical Wiring. Publised at Friday, January 19th 2018, 10:34:45 AM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Augustine Yvonne. Electrical Wiring. Publised at Friday, January 26th 2018, 00:12:32 AM. Ensure that identification tags and cable markers are legible, marked with a permanent ink and suitable for the environment where the panel is to be used. They should also correspond with those shown in the machine drawings and instruction or service documentation.
By Babette Benjamine. Electrical Wiring. Published at Saturday, January 20th 2018, 11:18:28 AM. A receptacle outlet is one in which one or more receptacles are installed for the purpose of attaching “plug and cord-connected” type devices, and a lighting outlet is one intended for a direct-wired connection to a lamp holder, luminaire (lighting fixture) or ceiling fan.
By Claudie Ulysse. Electrical Wiring. Published at Saturday, January 20th 2018, 10:22:35 AM. This section requires you to support conductors in panels to keep them in place. You're permitted to use wiring channels if they're made of a flame-retardant insulating material. If you're working with back-connected control panels, you must provide access doors or swing out panels that swing about a vertical axis. Multiple-device control panels must have terminal blocks or attachment plugs and receptacles to terminate and connect all outgoing control conductors.
By Annette Noele. Electrical Wiring. Published at Saturday, January 20th 2018, 03:31:50 AM. When the current is switched on or off, the electro-magnetic field increases and decreases, rapidly causing, in effect, a radio signal. The effect is similar to the crackle that can sometimes be heard on the radio or television when something like a fridge switches on and off. This radiated signal can be picked up by the other wires in the system and cause interference to the normal working voltages in the system
By Sylviane Marcelline. Electrical Wiring. Published at Saturday, January 20th 2018, 02:36:35 AM. In general, contactors should be kept away from electronic devices. A highly disturbing device (variable speed drive, frequency converter, etc.) will have less radiation in the panel if it is “encapsulated” in a small, electromagnetically sealed, unpainted metal enclosure.
By Augustine Yvonne. Electrical Wiring. Published at Saturday, January 20th 2018, 01:45:37 AM. After successful completion, the troubleshooter can improve their understanding of DC, AC, three phase circuits, Relays, Contactors, PLC, Electronics, and other related technology.
By Blandine Honorine. Electrical Wiring. Published at Saturday, January 20th 2018, 01:41:31 AM. Wiring diagrams show the connections to the controller. Wiring diagrams, sometimes called “main” or “construction” diagrams, show the actual connection points for the wires to the components and terminals of the controller.
By Augustine Yvonne. Electrical Wiring. Published at Friday, January 19th 2018, 21:33:17 PM. The terminations of shielded or screened conductors should be terminated so that the screen cannot fray. If the screen is to be connected then make it off in the same way as for coaxial cable with a soldered pigtail and a sleeve.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.