By Charline Rodrigue. Electrical Wiring. Publised at Sunday, December 10th 2017, 22:32:01 PM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Augustine Yvonne. Electrical Wiring. Published at Tuesday, January 30th 2018, 16:32:34 PM. Every type of machine has unique requirements when it comes to operator safety. From an electrical standpoint, industrial machine equipment and tools - from drill presses to multi-motored automatic machines.
By Claudie Ulysse. Electrical Wiring. Published at Tuesday, January 30th 2018, 12:02:29 PM. It would then be connected to the contactors and overload relays that constitute the motor starter. Two of the phases are also connected to the transformer to power the logic. The start and stop buttons are at the left of the box (note: normally these are mounted elsewhere, and a separate layout drawing would be needed).
By Linda Cerise. Electrical Wiring. Published at Tuesday, January 30th 2018, 08:35:58 AM. Where the circuits work at different voltages, the conductors must be separated by suitable barriers or all the wires insulated for the highest voltage to which any conductor may be subjected.
By Linda Cerise. Electrical Wiring. Published at Tuesday, January 30th 2018, 08:20:49 AM. You must totally enclose conductors and their connection external to the control panel enclosure in suitable raceways or enclosures. Unless used for flexible connections involving small or infrequent movements, or connections to normally stationary motors, limit switches and other externally mounted devices, fittings used with raceways or multiconductor cables must be liquidtight.
By Claudie Ulysse. Electrical Wiring. Published at Tuesday, January 30th 2018, 07:53:29 AM. For grounded control circuits, you may use a green (with or without one or more yellow stripes) or a bare conductor to connect the transformer terminal to a grounding terminal on the control panel.
By Annette Noele. Electrical Wiring. Published at Tuesday, January 30th 2018, 04:22:56 AM. The terminations of shielded or screened conductors should be terminated so that the screen cannot fray. If the screen is to be connected then make it off in the same way as for coaxial cable with a soldered pigtail and a sleeve.
By Annette Noele. Electrical Wiring. Published at Tuesday, January 30th 2018, 03:31:15 AM. Conductors and cables should run from terminal to terminal without any intervening joins. This refers to making a joint in the middle of a wire or cable. If it is necessary for any reason then use a suitable connector or terminal block. Don’t use a twisted and soldered joint.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.