By Claudie Ulysse. Electrical Wiring. Publised at Tuesday, September 19th 2017, 10:22:23 AM. Where the circuits work at different voltages, the conductors must be separated by suitable barriers or all the wires insulated for the highest voltage to which any conductor may be subjected.
By Charline Rodrigue. Electrical Wiring. Published at Saturday, January 27th 2018, 13:30:19 PM. The terminations of shielded or screened conductors should be terminated so that the screen cannot fray. If the screen is to be connected then make it off in the same way as for coaxial cable with a soldered pigtail and a sleeve.
By Linda Cerise. Electrical Wiring. Published at Saturday, January 27th 2018, 11:18:20 AM. Conductors and cables should run from terminal to terminal without any intervening joins. This refers to making a joint in the middle of a wire or cable. If it is necessary for any reason then use a suitable connector or terminal block. Don’t use a twisted and soldered joint.
By Claudie Ulysse. Electrical Wiring. Published at Saturday, January 27th 2018, 10:46:17 AM. The combined cross-sectional area of all conductors and cables is not permitted to exceed 50% of the interior cross-sectional area of the raceway. The fill provisions are based on the actual dimensions of the conductors or cables used.
By Linda Cerise. Electrical Wiring. Published at Saturday, January 27th 2018, 05:30:58 AM. You must totally enclose conductors and their connection external to the control panel enclosure in suitable raceways or enclosures. Unless used for flexible connections involving small or infrequent movements, or connections to normally stationary motors, limit switches and other externally mounted devices, fittings used with raceways or multiconductor cables must be liquidtight.
By Severin Theodore. Electrical Wiring. Published at Saturday, January 27th 2018, 01:24:41 AM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Augustine Yvonne. Electrical Wiring. Published at Friday, January 26th 2018, 22:36:40 PM. Workshops manufacturing parts in PVC or rubber use high-frequency welding processes to perform assembly. The propagation of strong magnetic fields and high-frequency waves is not easily controllable.
By Sylviane Marcelline. Electrical Wiring. Published at Friday, January 26th 2018, 17:15:25 PM. This section requires you to support conductors in panels to keep them in place. You're permitted to use wiring channels if they're made of a flame-retardant insulating material. If you're working with back-connected control panels, you must provide access doors or swing out panels that swing about a vertical axis. Multiple-device control panels must have terminal blocks or attachment plugs and receptacles to terminate and connect all outgoing control conductors.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.