By Annette Noele. Electrical Wiring. Publised at Tuesday, January 23rd 2018, 08:33:10 AM. Two or more conductors may only be connected to a terminal that is designed for the purpose. The majority of connecting blocks will only take one or two conductors. Don’t force in any more.
By Linda Cerise. Electrical Wiring. Publised at Sunday, February 04th 2018, 05:41:41 AM. When constructing junction boxes and pull boxes, you must be careful to exclude materials such as dust, flyings, oil and coolant. After you complete all wiring operations, you must seal all unused knockouts or openings.
By Severin Theodore. Electrical Wiring. Published at Wednesday, January 24th 2018, 17:28:44 PM. Soldered connections should be made only to terminals suitable for that purpose. Transformers may be fitted with turret tags suitable for soldering and printed circuit board assemblies may have solder pins.
By Charline Rodrigue. Electrical Wiring. Published at Wednesday, January 24th 2018, 14:48:05 PM. Where the circuits work at different voltages, the conductors must be separated by suitable barriers or all the wires insulated for the highest voltage to which any conductor may be subjected.
By Linda Cerise. Electrical Wiring. Published at Wednesday, January 24th 2018, 14:31:15 PM. Ensure that identification tags and cable markers are legible, marked with a permanent ink and suitable for the environment where the panel is to be used. They should also correspond with those shown in the machine drawings and instruction or service documentation.
By Charline Rodrigue. Electrical Wiring. Published at Wednesday, January 24th 2018, 13:27:55 PM. The combined cross-sectional area of all conductors and cables is not permitted to exceed 50% of the interior cross-sectional area of the raceway. The fill provisions are based on the actual dimensions of the conductors or cables used.
By Augustine Yvonne. Electrical Wiring. Published at Wednesday, January 24th 2018, 11:53:01 AM. Wires and cables (conductors) are insulated and protected by a variety of materials (insulators) each one having its own particular properties. The type of material used will be determined by the designer who will take into account the environment in which a control panel or installation is expected to operate as well as the application of individual wires within the panel.
By Sylviane Marcelline. Electrical Wiring. Published at Wednesday, January 24th 2018, 10:58:28 AM. When the current is switched on or off, the electro-magnetic field increases and decreases, rapidly causing, in effect, a radio signal. The effect is similar to the crackle that can sometimes be heard on the radio or television when something like a fridge switches on and off. This radiated signal can be picked up by the other wires in the system and cause interference to the normal working voltages in the system
By Claudie Ulysse. Electrical Wiring. Published at Wednesday, January 24th 2018, 10:54:28 AM. Conductors and cables should run from terminal to terminal without any intervening joins. This refers to making a joint in the middle of a wire or cable. If it is necessary for any reason then use a suitable connector or terminal block. Don’t use a twisted and soldered joint.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.