By Claudie Ulysse. Electrical Wiring. Publised at Tuesday, January 30th 2018, 07:53:29 AM. • Black represents ungrounded line, load and control conductors at line voltage. • Red represents ungrounded AC control conductors, at less than line voltage. • Blue represents ungrounded DC control conductors. • Yellow represents ungrounded control circuit conductors that may remain energized when the main disconnecting means is in the OFF position. These conductors must be yellow throughout the entire circuit, including wiring in the control panel and the external field wiring. • White or natural gray represents a grounded circuit conductor. • White with blue stripe represents a grounded DC current-carrying circuit conductor. International and European standards require you to use light blue for the neutral conductor. • White with yellow stripe represents grounded AC current-carrying control circuit conductors that remain energized when the disconnecting means is in the OFF position. For additional circuits powered from different sources that remain energized when the main disconnecting means is in the OFF position, you must use striping colors other than green, yellow or blue to uniquely identify the grounded conductors.
By Annette Noele. Electrical Wiring. Publised at Thursday, February 01st 2018, 07:32:39 AM. In general, contactors should be kept away from electronic devices. A highly disturbing device (variable speed drive, frequency converter, etc.) will have less radiation in the panel if it is “encapsulated” in a small, electromagnetically sealed, unpainted metal enclosure.
By Annette Noele. Electrical Wiring. Publised at Sunday, January 28th 2018, 19:28:59 PM. Wiring diagrams show the connections to the controller. Wiring diagrams, sometimes called “main” or “construction” diagrams, show the actual connection points for the wires to the components and terminals of the controller.
By Annette Noele. Engine Wiring. Published at Saturday, February 03rd 2018, 12:44:52 PM. Digital Multi-Meters come in two common varieties: Auto- Ranging, and Non Auto-Ranging. A non auto-ranging meter requires you to select a range of “sensitivity” for the given function you are using. For example if you want to measure resistance, you would need to select a range of up to 200 ohms, up to 20Kohms (20,000 ohms), 200Kohms, etc. An auto-ranging meter will automatically figure out the range and give you a measurement.
By Blandine Honorine. Electrical Wiring. Published at Saturday, February 03rd 2018, 12:21:42 PM. You are required to run conductors and cables from terminal to terminal without splices. However, an exception allows you to install a splice in leads attached to electrical equipment, such as motors and solenoids.
By Linda Cerise. Electrical Wiring. Published at Saturday, February 03rd 2018, 11:16:16 AM. A receptacle outlet is one in which one or more receptacles are installed for the purpose of attaching “plug and cord-connected” type devices, and a lighting outlet is one intended for a direct-wired connection to a lamp holder, luminaire (lighting fixture) or ceiling fan.
By Babette Benjamine. Electrical Wiring. Published at Saturday, February 03rd 2018, 10:26:59 AM. For grounded control circuits, you may use a green (with or without one or more yellow stripes) or a bare conductor to connect the transformer terminal to a grounding terminal on the control panel.
By Claudie Ulysse. Electrical Wiring. Published at Saturday, February 03rd 2018, 06:53:45 AM. After successful completion, the troubleshooter can improve their understanding of DC, AC, three phase circuits, Relays, Contactors, PLC, Electronics, and other related technology.
By Blandine Honorine. Electrical Wiring. Published at Saturday, February 03rd 2018, 03:20:28 AM. It would then be connected to the contactors and overload relays that constitute the motor starter. Two of the phases are also connected to the transformer to power the logic. The start and stop buttons are at the left of the box (note: normally these are mounted elsewhere, and a separate layout drawing would be needed).
By Charline Rodrigue. Electrical Wiring. Published at Saturday, February 03rd 2018, 02:17:12 AM. Wires and cables (conductors) are insulated and protected by a variety of materials (insulators) each one having its own particular properties. The type of material used will be determined by the designer who will take into account the environment in which a control panel or installation is expected to operate as well as the application of individual wires within the panel.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.