This section requires you to support conductors in panels to keep them in place. You're permitted to use wiring channels if they're made of a flame-retardant insulating material. If you're working with back-connected control panels, you must provide access doors or swing out panels that swing about a vertical axis. Multiple-device control panels must have terminal blocks or attachment plugs and receptacles to terminate and connect all outgoing control conductors.
Ensure that identification tags and cable markers are legible, marked with a permanent ink and suitable for the environment where the panel is to be used. They should also correspond with those shown in the machine drawings and instruction or service documentation.
D-42 - Engine Wiring Diagram Specialist
Copyright © 2003 - 2018 Domain Media. All sponsored products, company names, brand names, trademarks and logos arethe property of their respective owners.